A User ID is a user name and password that can be used to access several Honeywell Web sites.
Parallel Groove Clamp Tool
Cross Arm Gins are used on cross arms when only one
conductor needs to be raised. Use the arm gin to change
insulators; apply an armor rod to a conductor; raise a conductor
from a lower position to the cross arm, or lower the conductor.
The 2-1/2” (6.4 cm) diameter fiberglass pole has two eyes at
the top in which to hook the block line and tie back line. The
base fits a 4-3/4” x 5-7/8” (12.1 x 14.9 cm) cross arm. Included
shims are needed for smaller arms.
Ground Rod Drivers are 60” (1.52 m) long and drives
5/8” (1.6 cm) ground rods deep by concentrating impact
directly to the rod.
Light-weight and easy-to-use. Drives 1/2” (1.3 cm) ground
rods with less effort than conventional methods. Discs
surrounding the handle protect hands from walls, shrubbery,
and the sliding parts. Measures 26” (66 cm) long with a 14”
(35.6 cm) stroke.
The Temporary Transfer Arm is used to change crossarms,
insulators, or poles on short spans up to and including 15 kV phase
to phase. The mast (Cat. No. 1306M) is 2-1/2” in diameter by 6 feet
(1.82 m) long. The horizontal arm (Cat. No. 1340WHF8) is 2-1/2” in
diameter by 8 feet (2.44 m) long. The arm has a balanced load rating
of 600 lbs. (272 kgs); unbalanced at 150 lbs. (68 kgs). These units
are mounted to the pole using chain binders (Cat. No. 1304D) and
are rated for 15 kV without insulators and 35 kV with insulators.